Problem: High Level of TSS, Turbidity, Colour and Organic Matter.
Solution: Coagulation/Settling, MMF, UF, Disinfection.
The Clients requirement was to use the Lake Huma water supply as drinking water for the caravan park.
PWS designed and installed a packaged system to comply with the clients requirements and meet Australian Drinking Water Guidelines.
To design, manufacture and install a 7,000 L/Hr UF Membrane system, including suitable pretreatment and disinfection.
PWS designed, manufactured, installed and commissioned the water treatment plant.
Water is pumped from the Lake Huma to a holding tank while dosing coagulant. After sufficient contact time water is then pumped through the Multi-Media Filters, 1micron Cartridge filters and the Ultra-Filtration systems and finally disinfected with chlorine.
The filtered water is then stored in drinking water tanks for use.
The water treatment plant delivers filtered water that complies or exceed the Australian Drinking Water guidelines.